Air Conditioning Repair Contractor Mango Hill
Looking for the most reliable appliance, refrigeration equipment, and air conditioning repair contractor in Mango Hill?
Triple Point is the most reliable local services provider of appliance, refrigeration equipment, and air conditioning repair contractor Mango Hill, North Lakes, Brisbane, and the Sunshine Coast have come to rely on.
Have you been told your air conditioner needs to be replaced?
Most companies will not take the time to diagnose faulty systems properly and will push you to replace them. Our technicians at Triple Point Services are highly trained experts in electrical, electronics and refrigeration systems diagnosis and that is why we have become one of the most reliable air conditioning replacement contractor. Whether you need a split system air conditioning replacement or a ducted air conditioning repair, Triple Point is the company you call.
Repair of circuit boards is often much cheaper than replacement with new
We can diagnose the faults down to the individual control board and often the individual component on the electronic board. We can then replace the individual component on the board in house or send it away for more complicated repairs.
Case study 1 – APAC Sundowner repair
A customer had used two previous companies who had both stated that the outdoor electronic control board on an older Australian made APAC Sundowner ducted air conditioner was faulty and needed to be replaced, however, the part was no longer available.
The customer called Triple Point Services and explained the issue. We knew that this part was a common defrost control module and with minor modification a generic defrost control board would work. Not only that but with a short call to the supplier we knew the original (slightly updated) parts were available!
We asked the customer if we could perform our own diagnosis to ensure nothing else had been missed.
Within 5 minutes of arrival our technician found an open circuit high-pressure switch…
After being told to replace the system at a cost of around $15,000 we were able to fit a high-pressure micro switch to a disused valve port for a total cost of under $500. The ducted system was repaired and up and running within 15 minutes of our arrival.
Call us today on 0455518877 if you have any doubts about your ducted air conditioner.
Case study 2 – Panasonic air conditioner repair
We had a customer call about an intermittent fault with a wall split system. The customer had another air conditioning company out to inspect and were told something about a faulty indoor control module and that it’s not worth repairing so they should replace it.
We arrived, we checked the fault codes (pretty basic stuff here), we found the issue was faulty compressor temperature probe wiring. We replaced the wiring to the probe and guess what? From a potential $3000 replacement system to under $300 in labour.
Give us a call! 0455518877
Case study 3 – cheap Daikin ducted air conditioner repair
On multiple occasions, we have diagnosed the main inverter printed circuit board as faulty on mostly Daikin ducted systems. A design flaw has allowed a convenient shelf for rodents and insects to sit on and excrete onto the main inverter PCB below causing premature failure. We send these complicated boards away for repair rather than replacement and can save you upwards of $1000.
- Example costs:
- Brand new Daikin main inverter PCB with 12 months warranty:
- $2099 installed
- Repaired Daikin main inverter PCB with 12 months warranty:
- $999 installed
- Replacement of entire system:
Call us for all brands of inverter board repair!